[BLDG-SIM] Ground loop heat pumps + boilers.
mgangemi at WoodHarbinger.com
Wed Oct 25 07:51:33 PDT 2006
I understand that DOE2 (and therefore eQuest) doesn't handle boilers
connected to ground loop heat pumps. This is of course a problem, as
unless you have a very large ground loop in reality you need an
additional heat source. How I've decided to handle this is to use two
runs - one with a regular sized ground loop, and one with a ground loop
with 100x the area. I then take the heat energy difference, and use
that as my predicted boiler energy use (after adjusting for efficiency).
Basically, I'm assuming a boiler steps in to provide the capacity that
the heat pumps could use when they need it.
Does anyone see a problem with this strategy? I understand it misses
some of the finer details of a ground source system, but it seems like a
reasonable estimate of energy use. Is there a better way to do this?
-Matt Gangemi, P.E.
Wood Harbinger, Inc.
Mechanical / Electrical Engineers
3025 112th Avenue NE, Suite 200
Bellevue, WA 98004-8002
Phone: (425) 822-9499 ext. 188
Fax: (425) 822-1288
mgangemi at woodharbinger.com
You received this e-mail because you are subscribed
to the BLDG-SIM at GARD.COM mailing list. To unsubscribe
from this mailing list send a blank message to
BLDG-SIM-UNSUBSCRIBE at GARD.COM
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Bldg-sim