[Bldg-sim] zero cooling load in BEPS report
ramana.koti at gmail.com
Thu Mar 27 09:32:58 PDT 2008
The project is a mixed use building with offices and a hotel. The system is
VAV with chillers and cooling towers. The hotel rooms use fan coil units.
In eQUEST, after the condenser water loop is utilized for a water side
economizer loop for the office floors, the space cooling in the BEPS report
shows up as zero. Any ideas on what's going wrong? Any suggestions on
troubleshooting the issue are appreciated.
Ramana Koti, LEED AP
Sustainable Building Analyst
ELEMENTS division of BNIM architects
106 W. 14th Street Suite 200
Kansas City, Missouri 64105
p 816.783.1635 f 816.783.1501
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Bldg-sim