[Bldg-sim] Process Loads
oschwieterman at fhai.com
Fri Mar 18 13:24:22 PDT 2011
You can try but I really doubt if the reviewer will see it that way. I
always consider it its own HVAC system in the proposed model and lump it
in with the one system per floor HVAC system in the baseline model.
I do not see much of a benefit for counting this as a process load,
maybe you can explain why you want to do this.
From: Rob Hudson [mailto:rdh4176 at gmail.com]
Sent: Friday, March 18, 2011 3:23 PM
To: bldg-sim at lists.onebuilding.org
Subject: [Bldg-sim] Process Loads
I have a question about definition and correct interpretation. If I am
modeling building that has a space with a data rack and its own cooling
system separate from the rest of the buildings systems, is the cooling
considered process energy because it is "required" to be there similar
to the data rack electrical energy?
thanks in advanced,
Fanning/Howey Associates, Inc. intends to send this transmission (including any attachments) only to the
designated individual or entity. If you received this message in error, please notify the sender by replying
to the electronic mail (if electronic) or by telephone at the number indicated on this document.
Fanning/Howey Associates, Inc. has taken reasonable precautions to ensure no viruses are present in the
electronic mail. Fanning/Howey Associates, Inc., will not accept responsibility for any loss or damage arising
from the use of this electronic mail or attachments. Use, disclosure, dissemination, distribution, or reproduction
of this message by unintended recipients is not authorized and maybe unlawful. Any information included in
this transmission that is not related to contracts with our authorization, verbal or written, by Fanning/Howey
Associates, Inc. may not be covered by our professional liability insurance.
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Bldg-sim