[Bldg-sim] [Equest-users] Absorption Chiller Modeling
Vikram.Sami at perkinswill.com
Mon Dec 10 10:21:57 PST 2012
Absorption chillers should be able to run on water cooled condensers. Any chance we can see your inp file?
Vikram Sami, LEED AP BD+C
Sustainable Design Analyst
1315 Peachtree St. NE, Atlanta, GA 30309
t: 404-443-7462 f: 404.892.5823 e: vikram.sami at perkinswill.com www.perkinswill.com<http://www.perkinswill.com/>
Perkins+Will. Ideas + buildings that honor the broader goals of society
From: equest-users-bounces at lists.onebuilding.org [mailto:equest-users-bounces at lists.onebuilding.org] On Behalf Of ????
Sent: Monday, December 10, 2012 5:54 AM
To: Kushagra Juneja; equest-users
Subject: Re: [Equest-users] Absorption Chiller Modeling
you must keep it blank ,when the TYPE command is GAS-ABSOR.if want to model absorption chiller (water cooled condenser),you can create a condenser Loop,then modify the CW-LOOP to the Loop which you create just now.
------------------ Original ------------------
From: "Kushagra Juneja";
Date: 2012Äê12ÔÂ10ÈÕ(ÐÇÆÚÒ») ÍíÉÏ7:04
Subject: [Equest-users] Absorption Chiller Modeling
I am trying to model absorption chiller (water cooled condenser). But it gets stuck up at 18%. I am attaching the error screen shot that pops up while input.
Kushagra Juneja, IGBC AP, GRIHA T&E
LEED Green Asso.
Sustainability Engineer (E-II)
Kamal Cogent Energy Pvt. Ltd.
1st Floor, Kamal Ratan Chambers,
Opposite GPO, MI Road, Jaipur ¨C 302001
Ph.: 0141-2373184/85, Ext.: 234
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Bldg-sim