[Bldg-sim] Baseline chiller curves
jra_sac at yahoo.com
Sun Feb 26 00:05:08 PST 2012
Hi Ratha Shree..
This is only my opinion.
I would only worry about the Chiller COP or kW/ton. You cannot create an IPLV curve unless you know the kW/ton at the 100%, 75%, 50%, and 25% points. Otherwise, it is one equation and three unknowns 9you DO know the 100% point).
I believe the DOE-2 curves are good enough for the Baseline, having been through 1000s of analysis in the private and governmental sectors.Unless ASHRAE can PROVIDE those four aforementioned points.
From: Rathna Shree <rathnashreep at yahoo.in>
To: bldg <bldg-sim at lists.onebuilding.org>
Sent: Friday, February 24, 2012 11:19 PM
Subject: [Bldg-sim] Baseline chiller curves
Similar discussion have happened on this subject. But still couldn't get clarity so i am posting the question again.
There are a number of default chiller curves available in Visual doe or equest software. But do we have to construct a baseline chiller curve and input for the base case? How to make sure ASHRAE 90.1 IPLV is captured for the chiller in baseline case?
Bldg-sim mailing list
To unsubscribe from this mailing list send a blank message to BLDG-SIM-UNSUBSCRIBE at ONEBUILDING.ORG
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Bldg-sim