[Equest-users] Running FCU Units on a Dry Cooler
B.Burns at ha-inc.com
Mon Dec 17 11:11:51 PST 2012
Doesn't the dry cooler have some sort of heat pump or chiller to take heat from the space and reject it to the condensing loop?
Byron D. Burns
From: equest-users-bounces at lists.onebuilding.org [mailto:equest-users-bounces at lists.onebuilding.org] On Behalf Of Ömer Moltay
Sent: Monday, December 17, 2012 1:43 PM
To: bfountain at greensim.com; eQUEST Users List
Subject: Re: [Equest-users] Running FCU Units on a Dry Cooler
Didn't get that to work unfortunately. I always have zero flow on my condenser loop attached to the waterside economizer.
Wouldn't it also be possible to model water cooled chillers with zero energy consumption (EIR=0) and than the only energy used by the system would the dry cooler fans?
17.12.2012 19:42 tarihinde, bfountain at greensim.com yazdı:
> Try creating a chiller of type waterside economizer between the CHW & CW loops.
> ------Original Message------
> From: Ömer Moltay
> Sender: equest-users-bounces at lists.onebuilding.org
> To: eQUEST Users List
> ReplyTo: omoltay at mimtarch.com
> Subject: [Equest-users] Running FCU Units on a Dry Cooler
> Sent: Dec 17, 2012 10:56 AM
> Dear All,
> How do you suggest the modeling of a building where FCU units are
> provided with chilled water from dry coolers? Dry coolers can only be
> modeled as heat rejection devices on condenser loops. FCU units have
> to be assigned a chilled water loop. Is there a way to model this?
> Omer Moltay
> Equest-users mailing list
> To unsubscribe from this mailing list send a blank message to
> EQUEST-USERS-UNSUBSCRIBE at ONEBUILDING.ORG
> Brian Fountain
> bfountain at greensim.com
Equest-users mailing list
To unsubscribe from this mailing list send a blank message to EQUEST-USERS-UNSUBSCRIBE at ONEBUILDING.ORG
More information about the Equest-users