[Equest-users] Problem in simulate a heat-pump chiller with cooling tower
slv3sat at gmail.com
Thu Mar 29 08:12:19 PDT 2012
Is this a regular chiller and and are you using heat recovered from it to
heat the hw loop? If yes, you can use the heat recovery field on the
chiller tab and set it to the hw loop, with the heat recovery % at 80%-85%.
2012/3/21 Jimmy Law <lawchh at gmail.com>
> Dear all,
> Recently I am trying to do heat-pump screw chiller with a fluid cooling
> tower for a commercial building in a sub-tropical area, which means it will
> mostly run like a normal chiller and will supply HW in 40 degreeC for
> heating in just two or three month. Meanswhile, whenever I chose Loop-Loop
> Heat Pump and just Heat Pump for chiller type, the chiller obviously can
> not be connected to the CW loop but only to LAKE/WELL loop. Can anyone
> please give me any advice to solve this issue and simulate this system?
> Thank you!
> Jimmy Ching Hin LAW
> Mechanical Engineer, LEED Green Associate
> Equest-users mailing list
> To unsubscribe from this mailing list send a blank message to
> EQUEST-USERS-UNSUBSCRIBE at ONEBUILDING.ORG
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Equest-users