[Equest-users] Kitchen MAU/Exhaust
slv3sat at gmail.com
Tue Oct 9 12:51:13 PDT 2012
I am modelling a typical office building for EPACT which has a cooking
school also. It has 4 MAU's (10 HP each) and 2 exhaust fans (35 HP total).
The MAU's have chilled water coil and electric heating. How would one deal
with this in the baseline per APP G 2004 and ASHRAE 2001. Is this either
system 4 and has heat recovery or would it be same in both baseline and
Thanks for any insights.
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Equest-users