[Equest-users] Differential pressure reset on CHW Loop
julien.marrec at gmail.com
Tue Sep 22 12:52:20 PDT 2015
Do you have a variable speed pump? More importantly do you have two way valves?
Envoyé de mon iPhone
> Le 22 sept. 2015 à 21:00, Kusum Sekhalia <skusum3 at gmail.com> a écrit :
> I am trying to capture pumping energy savings attributed to applying differential pressure reset on CHW loop. I am changing the head set point control from fixed to valve reset in parametric runs but I don't see any energy savings. I even tried changing the sensor location from "entering loop" to "at coils" but no luck. Can anyone help in figuring out why I am not getting savings. Thanks!
> Equest-users mailing list
> To unsubscribe from this mailing list send a blank message to EQUEST-USERS-UNSUBSCRIBE at ONEBUILDING.ORG
More information about the Equest-users