[Date Prev][Date Next][Thread Prev][Thread Next][Date Index][Thread Index]
[EnergyPlus_Support] Re: vav with humidifier in zone equipment
The humidifier needs to be placed in main air loop branch just
upstream of the zone equipment. See example file CVRHMinHum.idf
--- In EnergyPlus_Support@xxxxxxxxxxxxxxx, Christian Struck
> Dear E+ user,
> could you please help out!
> I am trying to modify the VAVSingleDuctReheat model by introducing an
> humidifier behind the reheater to control the space humidity.
> Since the reheater is part of the zone equipment I am curious if I
> able to add the humidifier at all considering the code structure?
> Your response would be greatly appreciated!
> This message has been scanned for viruses by MailControl -
The primary EnergyPlus web site is found at:
The group web site is:
Attachments are not allowed -- please post any files to the appropriate folder in the Files are of the Support Web Site.
-- please post any files to the appropriate folder in the Files are of the Support Web Site.
Yahoo! Groups Links
<*> To visit your group on the web, go to:
<*> To unsubscribe from this group, send an email to:
<*> Your use of Yahoo! Groups is subject to: