[Date Prev][Date Next][Thread Prev][Thread Next][Date Index][Thread Index]
[EnergyPlus_Support] Re: sos!!!There is no results!!!Why???
Thank you very much,Mike.
This is my first overall simulation(^_^).With your help,the results
appear,but these results shake in one's shoes.I add report
variable :'Zone-Total Internal Latent Gain','Zone-Total Internal
Radiant Heat Gain','Zone-Total Internal Convective Heat Gain','Zone-
Total Internal Visible Heat Gain'.Take zone 'Hall' as a example,these
values are very very big,such as:3620462,6455492,5955262,806760,etc.
--- In EnergyPlus_Support@xxxxxxxxxxxxxxx, "Michael J. Witte"
> The file is set up to simulate 15 Jan and 15 Jul, with the
> UseWeatherFile, !- Day Of Week For Start Day
> Yes, !- Use WeatherFile Holidays/Special
> Yes, !- Use WeatherFile DaylightSavingPeriod
> The two days which are being simulated, apparently fall on the
> nearly everything in this simulation is scheduled off on weekends.
> extending the RunPeriods to a full week each, results appear.
> Note that standard EnergyPlus weather files have no holidays or
> savings time defined. If you have not added these to your epw
file, then you
> must specify them in the idf file using the SpecialDayPeriod and
> DaylightSavingPeriod objects.
> The condenser loop is not drawing in the HVAC Diagram output. This
> that the condenser loop still has a connection error. The
> Outlet Node Name in the CONDENSER LOOP object is incorrect. It
> The activity level schedule for the PEOPLE is always 0.398. This
is much too
> low. These values should be in the range of 40 to 1000 W/person.
> In PLANT OPERATION SCHEMES,cooling scheme, the load scheme name is
> This must be "cooling load range" so that the chiller can operate.
> On 1 Dec 2004, at 12:17, hbn_pch wrote:
> > Dear all,
> > I'am in despair.According to Mike's hint,i check the idf more
> > more times.But i can't find the problem.Cry!There is no results
> > zone and primary system.In other words,i'am unsuccessful.
> > I've uploaded the idf(example.zip).Appreciated your kind help!
> > The primary EnergyPlus web site is found at:
> > http://www.energyplus.gov
> > The group web site is:
> > http://groups.yahoo.com/group/EnergyPlus_Support/
> > Attachments are not allowed -- please post any files to the
> > in the Files area of the Support Web Site.
> > Yahoo! Groups Links
> Michael J. Witte, GARD Analytics, Inc.
> EnergyPlus Testing and Support
------------------------ Yahoo! Groups Sponsor --------------------~-->
Make a clean sweep of pop-up ads. Yahoo! Companion Toolbar.
Now with Pop-Up Blocker. Get it for free!
The primary EnergyPlus web site is found at:
The group web site is:
Attachments are not allowed -- please post any files to the appropriate folder in the Files area of the Support Web Site.
Yahoo! Groups Links
<*> To visit your group on the web, go to:
<*> To unsubscribe from this group, send an email to:
<*> Your use of Yahoo! Groups is subject to: