[Equest-users] eQuest unmet load and report help
ssavich at systemswestengineers.com
Mon Aug 4 12:52:17 PDT 2008
Can you post your .inp and .pd2 files?
Systems West Engineers
411 High Street
Eugene, OR 97401-2427
(541) 342-7220 (fax)
From: equest-users-bounces at lists.onebuilding.org
[mailto:equest-users-bounces at lists.onebuilding.org] On Behalf Of Marcus
Sent: Monday, August 04, 2008 12:34 PM
To: equest-users at lists.onebuilding.org
Subject: [Equest-users] eQuest unmet load and report help
I am working on a LEED submission, and I am seeing a very large % of hours
any system zone outside throttling range but zero percent of the plant load
is unsatisfied. Can someone explain what exactly the difference in these
numbers is? Also, does anybody have any idea what might cause such a large
discrepancy. My first thoughts were undersized equipment, but I'm hesitant
to lay blame on the HVAC contractor until I have fully verified my model.
Also, for LEED, they want the ES-D reports. It seems that for some of my
models .sim outputs, the ES-D report is not included, but is included for
others. Any thoughts?
Thank you for your help.
Essex Engineering Corporation
meliason at essexco.com
Equest-users mailing list
To unsubscribe from this mailing list send a blank message to
EQUEST-USERS-UNSUBSCRIBE at ONEBUILDING.ORG
More information about the Equest-users