[Equest-users] Increase in roof insulation increases cooling load.
glenn.haynes at rlw.com
Fri Dec 19 09:44:54 PST 2008
If your building is in Columbus, you will have relatively mild cooling
seasons. If you request hourly output for your baseline and retrofit
runs and subtract to obtain hourly "savings", you will find that when
the outside temperature is well below the indoor temperature, you will
see negative "savings" due to the reduction in "free cooling" through
the roof system. If these negative "savings" more than offset the
positive savings, you will obtain a net negative "savings" overall.
From: equest-users-bounces at lists.onebuilding.org
[mailto:equest-users-bounces at lists.onebuilding.org] On Behalf Of Cyrus
Sent: Friday, December 19, 2008 10:34 AM
To: equest-users at lists.onebuilding.org
Subject: [Equest-users] Increase in roof insulation increases cooling
In a parametric run the roofing insulation was increased from U= 0.063
to U=0.033. by increasing the thickness of the "Insul Bd 2in (HF-B3)" of
the built up roof from 0.28 to 0.64.
In my results the HVAC cooling load increased by 4% and my heating load
decreased by 4%. Overall the net change was -1% energy savings.
Is this reasonable?
Cyrus Grimes, LEED(r) AP .
1108 City Park Avenue, 3rd Floor
Columbus, Ohio 43206
Phone (614) 443-1178 ext. 274
Fax: (614) 443-1594
e-mail: cgrimes at dynamix-ltd.com
P Please consider the environment before printing this e-mail note
IMPORTANT: This communication, together with any attachments hereto or links contained herein, is for the sole use of the intended recipient(s) and may contain information that is confidential and/or legally protected and privileged. If you are not the intended recipient, you are hereby notified that any review, redisclosure, copying, dissemination, distribution, forwarding, printing or use of this communication or its attachments is STRICTLY PROHIBITED. If you have received this communication in error, please notify the sender immediately by return e-mail message and delete the original and all copies of the communication, along with any attachments hereto or links herein, from your system. If you disclose this communication to any person or entity without our prior written consent, you may be subject to an action for breach of confidentiality, in addition to all other actions in law and in equity.
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Equest-users