[Equest-users] modelling water to water heat pumps from ground loopto radiant heating and cooling
bbishop at PathfinderEngineers.com
Wed Jul 22 12:03:47 PDT 2009
One thing you can do is to manually adjust the FLOOR-WEIGHT for each
space, especially if this is radiant slab, to "give a longer lag time
between heat gains and resultant cooling loads, and greater damping of
peak loads". [From the help menu text.]
William Bishop, EIT, LEED(r) AP | Pathfinder Engineers & Architects LLP
134 South Fitzhugh Street
Rochester, NY 14608
T: (585) 325-6004 Ext. 114
F: (585) 325-6005
bbishop at pathfinderengineers.com
P Please strive to live sustainably.
From: equest-users-bounces at lists.onebuilding.org
[mailto:equest-users-bounces at lists.onebuilding.org] On Behalf Of Peter
Sent: Wednesday, July 22, 2009 2:33 PM
To: equest-users at lists.onebuilding.org
Subject: [Equest-users] modelling water to water heat pumps from ground
loopto radiant heating and cooling
Any suggestions on how to set up radiant heating and cooling sourced
from a ground loop?
I am nervous about using water to air units and zeroing out the fan
energy but that's where we are starting. Will the loads calculate
properly where heating setpoints are in the low 60's?
Any help at all would be super.
Thanks in advance!
Peter W. LeMessurier, P.E., LEED AP
Beaudin Ganze Consulting Engineers
P 303.278.3820 x 5231
76% of Staff LEED Accredited Professionals!
Please consider the environment before printing
This message has been scanned for viruses and
dangerous content by MailScanner <http://www.mailscanner.info/> , and is
believed to be clean.
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Equest-users