[Equest-users] Baseline Heat Recovery
wbishop at pathfinder-ea.com
Thu Dec 1 06:37:45 PST 2011
I would set ERV-LATENT-EFF to 0.50.
Additionally, if the baseline system is required to have an economizer
per G126.96.36.199, I would meet the G188.8.131.52 requirement "to bypass or
control the heat-recovery system to permit air economizer operation,
where applicable", by setting ERV-RUN-CTRL to WHEN-MIN-OA.
I guess it is a judgment call how to set all the other ERV variables.
Typically, I set them identical to the proposed ERV if there is one.
From: equest-users-bounces at lists.onebuilding.org
[mailto:equest-users-bounces at lists.onebuilding.org] On Behalf Of
omoltay at mimtarch.com
Sent: Wednesday, November 30, 2011 10:06 AM
To: equest-users at lists.onebuilding.org
Subject: [Equest-users] Baseline Heat Recovery
How would you recommend modeling in eQuest the G184.108.40.206 requirement
its request that "50% energy recovery effectivness shall mean a change
the enthalpy of the outdoor air supply equal to 50% of the difference
between the outdoor air and return air at design conditions"?
Equest-users mailing list
To unsubscribe from this mailing list send a blank message to
EQUEST-USERS-UNSUBSCRIBE at ONEBUILDING.ORG
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Equest-users