[Equest-users] how to decide the effficency of HVAC equipment
Oscar Buchely L.
obuchely at ses-ingenieria.com
Mon Apr 23 09:50:01 PDT 2012
I have a similar question, If my system is 2 (PTHP) can I use table
6.8.1B or 6.8.1D and why?
On 22/04/2012 08:32 a.m., Dave Weigel wrote:
> 6.8.1A is appropriate for packaged systems.
> The other table (6.8.1D) applies to single-room air conditioners.
> Best to you,
> *From:* ???? <mailto:546751190 at qq.com>
> *Sent:* Saturday, April 21, 2012 3:09 AM
> *To:* equest-users <mailto:equest-users at lists.onebuilding.org>
> *Subject:* [Equest-users] how to decide the effficency of HVAC equipment
> Dear all
> When using appendix G of ASHRAE 90.1-2007 to build baseline, If the
> baseline system is system 3 (PSZ-AC) , 4 (PSZ-HP) or 5 (Packaged VAV
> with reheat) ,which table in ASHRAE90.1-2007 should be used to decide
> the Equipment efficiency separately? Table 6.8.1A or 6.8.1D?
> Thank you for your help
> Equest-users mailing list
> To unsubscribe from this mailing list send a blank message to EQUEST-USERS-UNSUBSCRIBE at ONEBUILDING.ORG
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Equest-users