[Equest-users] Central Chilled Water Plant Serving BuildingOutside the LEED Boundary Area
503271081 at qq.com
Wed Jul 25 04:26:50 PDT 2012
you can reference to 2.4.2 in "Treatment of District or Campus Thermal Energy in LEED"
------------------ Original ------------------
From: "Chris Jones";
Date: 2012年7月24日(星期二) 晚上10:32
To: "Wallie Padero"; "equest-users";
Subject: Re: [Equest-users] Central Chilled Water Plant Serving BuildingOutside the LEED Boundary Area
Have you read the DES documentation from the USGBC? I believe you
have to follow those protocols.
At 01:44 AM 24/07/2012, Wallie Padero wrote:
>Dear E-quest users,
>I'm currently modeling a new construction building served by a
>central chilled water plant. The central chilled water plant also
>serves building outside the LEED boundary area. The total capacity
>of the central chilled water plant is approximately 1370 TR (Two 685
>TR Water Cooled Chillers) but the building i'm modeling within the
>LEED boundary is just 150 TR.
>Is this under DES? But i don't have any idea on what chilled water
>utility rate should be used?
>Please help me on what modeling strategy should be done on this case?
>Thanks in advance.
>Equest-users mailing list
>To unsubscribe from this mailing list send a blank message to
>EQUEST-USERS-UNSUBSCRIBE at ONEBUILDING.ORG
Christopher Jones, P.Eng.
Suite 1801, 1 Yonge Street
Toronto, ON M5E1W7
email cj at enersave.ca
Equest-users mailing list
To unsubscribe from this mailing list send a blank message to EQUEST-USERS-UNSUBSCRIBE at ONEBUILDING.ORG
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Equest-users