[Equest-users] system type workaround dilemma
robbyoylear at gmail.com
Fri May 4 08:45:13 PDT 2012
The Power Induction Unit system should meet your needs. When you select
the system at first it asks for a Chilled Water Loop but you can then
change it to DX Cooling and delete the CHW loop. The zone induction units
can be set at the zone level under the airflow tab.
On Fri, May 4, 2012 at 8:31 AM, Rob Hudson <rdh4176 at gmail.com> wrote:
> does both the VAV RTU and the PIU serve the same spaces or is it a
> core/shell design?
> On Fri, May 4, 2012 at 11:28 AM, Ramana Koti <ramana.koti at gmail.com>wrote:
>> Dear All,
>> I'm starting to build a LEED energy model. Its a small university
>> classroom building around 5000 sf. The proposed mechanical design is as
>> Packaged VAV RTU with DX cooling and natural gas heating. Twelve PIU
>> terminals with electric heating coils.
>> For the proposed design model, I'm unable to select a system type or
>> think of an equivalent/workaround in eQUEST. Any ideas on how best to go
>> about it or if it is doable in eQUEST at all?
>> Ramana Koti.
>> Equest-users mailing list
>> To unsubscribe from this mailing list send a blank message to
>> EQUEST-USERS-UNSUBSCRIBE at ONEBUILDING.ORG
> Rob Hudson
> Equest-users mailing list
> To unsubscribe from this mailing list send a blank message to
> EQUEST-USERS-UNSUBSCRIBE at ONEBUILDING.ORG
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Equest-users