jmcclanathan at CDiengineers.com
Thu Oct 18 09:00:28 PDT 2012
You can enter the design cfm at the zone level.
Jeremy McClanathan, P.E., BEMP, HFDP, LEED® AP BD+C
19203 36th Avenue W, Suite 200, Lynnwood, WA 98036
P 425-672-1071 | F 425-778-8769
??Please consider the environment before printing this email.
From: sambhav tiwari [mailto:tiwari.sambhav at gmail.com]
Sent: Thursday, October 18, 2012 12:44 AM
Subject: [Equest-users] FCU
When i am using FCU as Fan coil in system type my fan supply cfm tab is showing n/a also then fan control is tab is showing n/a which means that i can not enter design cfm in my supply cfm tab.
Any suggestion for this
Equest-users mailing list
To unsubscribe from this mailing list send a blank message to EQUEST-USERS-UNSUBSCRIBE at ONEBUILDING.ORG
This email message, including any attachments, is for the sole use of the intended recipient and may contain confidential, proprietary, and/or privileged information, as well as content subject to copyright and other intellectual laws. If you are not the intended recipient, you may not disclose, use, copy, or distribute the email message or its attachments. If you believe you have received this email message in error, please contact the sender by reply email, immediately delete this email and destroy copies.
More information about the Equest-users