[Equest-users] Non conditioned regularly occupied space
DEldridge at grummanbutkus.com
Fri Aug 30 04:01:53 PDT 2013
Just to clarify - does the remaining 95,000 ft2 of regularly occupied office have an engineered natural ventilation scheme?
There are some cases where 90.1 asks for cooling systems to be modeled even if none are proposed. You'll need to find out if those conditions apply to you.
On Aug 30, 2013, at 4:06 AM, "vamshi ranga" <vamshiranga at gmail.com> wrote:
> Dear All,
> We are modeling Non residential building for USGBC New Construction rating, which has regularly occupied (office) area of 100000 sq ft, out of which only 5000 sq ft of the regularly occupied (office) area is conditioned with VRV systems.
> Could you please let us know how the conditioned area shall be considered in Baseline and Proposed case. my doubts is,
> Shall this be modeled with 5000 sq ft conditioned area in both Base and Proposed or Is there any minimum requirement for percentage conditioned area?
> Equest-users mailing list
> To unsubscribe from this mailing list send a blank message to EQUEST-USERS-UNSUBSCRIBE at ONEBUILDING.ORG
More information about the Equest-users