[Equest-users] Specifying heat index in eQUEST
CBaker at cci-alliance.com
Fri Mar 6 02:21:35 PST 2015
The only thing I can think of would be to refer to the weather file data which relative humidity data would be there? You could also reference historical weather data to determine what months or weeks would likely exceed the minimum allowable relative humidity by the system controls and customize the scheduled on time to coincide with that.
In this case one could maintain the dry bulb setting like you normally would in equest and the system still takes relative humidity into account - at least as a function of outside air intake.
This might avoid more complex approaches but it would ensure you aren't getting unexpected simulation output.
I'm not an expert though! Lol.
Good luck Prasad!
- Chris in Alaska
Sent from my iPad
On Mar 5, 2015, at 7:07 PM, Prasad S Wani <p_s_wani at ateindia.com<mailto:p_s_wani at ateindia.com>> wrote:
I am modelling a building with a HVAC system to maintain it at certain dry bulb temperature (DBT) & relative humidity. In eQUEST, DBT & relative humidity control can be specified.
Whether it is possible to specify heat index (function of DBT & relative humidity) as controlling parameter in eQUEST ?
Kindly share your thoughts about it.
Equest-users mailing list
To unsubscribe from this mailing list send a blank message to EQUEST-USERS-UNSUBSCRIBE at ONEBUILDING.ORG<mailto:EQUEST-USERS-UNSUBSCRIBE at ONEBUILDING.ORG>
CCI-Alliance Confidentiality notice: This message is intended only for the person to whom addressed in the text above and may contain privileged or confidential information. If you are not that person, any use of this message is prohibited. We request that you notify us by reply to this message, and then delete all copies of this message including any contained in your reply. Thank you.
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Equest-users