[Hap-users] LEED System type 5: Supply Air Temp Reset
orlinvelin at hotmail.com
Thu Nov 8 04:54:47 PST 2012
I have similar question on how do you simulate chilled water reset which is required for the baseline model? Actually I have a comment from USGBC on this!
Sent from my iPad
On Nov 5, 2012, at 9:14 AM, "Matthew Scott" <MScott at nefisher.com> wrote:
> For LEED baseline system type 5, the Supply Air Temperature for cooling “shall be reset higher by 5 degrees F under the minimum cooling load conditions.”
> I take this to mean under Capacity Control, I should select “Temp Reset by Greatest Zone Demand” and set the Max Supply Temperature to 60 degrees since I have the Supply Temp set to 55 degrees. Reading the Help description on this setting makes me think otherwise, but there doesn’t appear to be a better option.
> I’ve attached a screen shot of the cooling settings:
> Perhaps the tech team could post a guide on how to properly execute all of the LEED / Appendix G requirements for each system type in HAP.
> Thanks for your help!
> Matt Scott
> N.E. Fisher & Associates, Inc.
> 329 East Second St, 2nd Flr
> Boyertown, PA 19512
> e: mscott at nefisher.com
> p: 610-369-3190
> f: 610-369-3194
> Hap-users mailing list
> To unsubscribe from this mailing list send a blank message to HAP-USERS-UNSUBSCRIBE at ONEBUILDING.ORG
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Hap-users