[TRNSYS-users] A few questions about Type 941
zhe.li at dit.ie
Wed Mar 26 08:35:37 PDT 2014
Dear David and all users,
Thanks for your time.
I have a few questions about air-to-water heat pump type 941.
I have the weather generator connected with the type 941 which Percent
Relative Humidity ( type 54) is linked with Inlet Air %RH (type 941). Is
this correct? I believe I have inputted the accurate monthly humidity ratio
as required in weather generator (Type 54), however, the output of Percent
Relative humidity looks quite small (less than 20%). I don't think that's
>From my understanding that the Type 941 neglect the effect of humidity
effect. However, as I read the proforma of this component, it does state
that Type 941 takes either relative humidity or humidity ratio as an input.
so is the relative humidity actually taking into consideration in the
The catalog provided for Type 941 is a generic catalog for this type of
heat pump as I assumed. Has it taken into consideration of defroze of
evaporate coil? It will be great if this is the case.
Thank you very much for your help. It is very important for me.
This email originated from DIT. If you received this email in error, please
delete it from your system. Please note that if you are not the named
addressee, disclosing, copying, distributing or taking any action based on
the contents of this email or attachments is prohibited. www.dit.ie
Is ó ITBÁC a tháinig an ríomhphost seo. Má fuair tú an ríomhphost seo trí
earráid, scrios de do chóras é le do thoil. Tabhair ar aird, mura tú an
seolaí ainmnithe, go bhfuil dianchosc ar aon nochtadh, aon chóipeáil, aon
dáileadh nó ar aon ghníomh a dhéanfar bunaithe ar an ábhar atá sa
ríomhphost nó sna hiatáin seo. www.dit.ie
Tá ITBÁC ag aistriú go Gráinseach Ghormáin - DIT is on the move to
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the TRNSYS-users