[Bldg-sim] mandatory provisions for a heat pump
cj at enersave.ca
Sat Dec 22 19:14:41 PST 2012
This is the only one that I could find.
ANSI.AHRI Standard 550-590 (I-P) with Addendum 1.pdf
At 05:16 AM 20/12/2012, francesco.passerini at inwind.it wrote:
>For a LEED certification I have to verify mandatory provisions of ASHRAE
>90.1-2007 for a heat pump that outside the building exchanges heat with
>the external air and it exchanges heat with the building, i.e. with the
>internal part of the HVAC plant, through water. The scheme of the plant is
>like as follows:
>The heat pump works both in heating mode (winter season) and in cooling
>mode (summer season).
>I wonder what tables I shall consider to respect the mandatory provisions.
>I thought that I have to consider Table 6.8.1B, in particular âAir cooled
>(cooling mode)â and âAir cooled (heating
>mode)â but I read in the relative
>technical standards, see ARI Standard 340/360 Table 3. and ARI 210/240
>Table 3., that as âINDOOR SECTIONâ only âair enteringâ is considered.
>I wonder even whether I have consulted the correct versions of the ARI
>standards. I have consulted the following links:
>Thank you for your attention.
>Bldg-sim mailing list
>To unsubscribe from this mailing list send a
>blank message to BLDG-SIM-UNSUBSCRIBE at ONEBUILDING.ORG
Christopher Jones, P.Eng.
Suite 1801, 1 Yonge Street
Toronto, ON M5E1W7
email cj at enersave.ca
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Bldg-sim