[Equest-users] Modeling VRV System
danielk at arborus.ca
Mon Mar 12 06:52:24 PDT 2012
On the subject of modelling VRF systems, I recently did some tests on a box-model in Ontario (climate zone 6) and compared the results of using PVVT and the WSHP systems. I found that the ability to use variable speed compressors in the PVVT systems – which are not available to the WSHP systems – made a huge difference to the energy savings and that the PVVT performed much better than the WSHP. In this case I was modelling the Mitsubishi system with no heat recovery and was using the performance curves from the “Application for Adoption of Variable Refrigerant Flow Systems Under the Tile 24-2008 Nonresidential ACM Procedures”.
Your mileage may vary, and I would strongly recommend building a test building using the wizard that allows you to test your performance curves and VRF modelling approach to make sure you are getting the results you are looking for.
Daniel Knapp, PhD, LEED® AP O+M
danielk at arborus.ca
Energy Strategies for the Built Environment
76 Chamberlain Avenue
Ottawa, ON, K1S 1V9
Phone: (613) 234-7178 ext. 113
Fax: (613) 234-0740
On 2012-03-12, at 9:37 AM, Michael Marvin wrote:
> Hi Everyone,
> I know that there’s been some chatter about this in the past, but has anyone determined a good way to simulate a VRV system accurately in eQuest? I’ve seen posts where some people have recommended using PVVT or the Water Heat Pump System, but I’m curious to hear if anyone has found a workaround that they feel works better than the others.
> Michael Marvin, LEED AP
> Buro Happold
> 100 Broadway
> New York, NY 10005
> Tel: (+1) 212 334 2025
> Email: michael.marvin at burohappold.com
> This transmission is confidential and intended solely for the person or organisation to whom it is correctly addressed. If you are not the intended recipient of this transmission, you should not take any action in reliance on it.Further, this transmission may contain confidential design and other information owned by Buro Happold Ltd. You should not copy, distribute, use, offer for sale or hire such information or in any way infringe the design and intellectual property rights of Buro Happold Ltd. It is intended that communication by email from Buro Happold Ltd or its employees is limited to communications connected to the services provided by Buro Happold Ltd. Buro Happold Ltd accepts no liability for any communications not connected to the services it provides. Computer viruses may be transmitted or downloaded onto your computer system via email communication. It is the recipient’s responsibility to take any action necessary to prevent computer viruses being transmitted in this way. Accordingly, Buro Happold Ltd dsclaims all responsibility which arises directly or indirectly from such transmission of computer viruses. Buro Happold Ltd. Registered in England: 2049511. Registered Office: Camden Mill, Lower Bristol Road, Bath BA2 3DQ.
> Equest-users mailing list
> To unsubscribe from this mailing list send a blank message to EQUEST-USERS-UNSUBSCRIBE at ONEBUILDING.ORG
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Equest-users