[Date Prev][Date Next][Thread Prev][Thread Next][Date Index][Thread Index]
[EnergyPlus_Support] HVAC/Equipment Specification, Limits?
Is there any limit of number of loops, branches (50), and nodes? Can
E+ have multiple CHW loop? Can chillers running in series?
The flow resolver is based on the following assumptions and
Each loop is only allowed to have a single splitter
and a single mixer.
Due to the fact that there can only be one splitter
and one mixer on a given loop, it follows logically that there can be at
most one bypass on each loop
No other components may be in series with a bypass,
i.e., a branch that contains a bypass may have no other equipment on that
Equipment may be in parallel only between the splitter
and mixer component of a loop or between one of those types of equipment
and the loop inlet/outlet nodes
Equipment may be hooked together in series in each
branch of the loop
Loops may have several inlet nodes or several outlet
Flow rates on individual branches will be
controlled using maximum and minimum available flow rate limits
To unsubscribe from this group, send an email to:
The primary EnergyPlus web site is found at:
Your use of Yahoo! Groups is subject to the Yahoo! Terms of Service.