the minimum and maximum setpoint managers: calculate the humidity ratio setpoints based on the humidification/dehumidifcation load of the zone and place the humidity ratio setpoints on the user defined nodes/nodelist in the minimum and maximum humidity setpoint managers objects. The humidication/dehumidification loads are calculated based on the Relative Humidities specified for the zone air. Therefore, the above schedule objects are not required and used incorrectly.
Also, run for typical winter and summer days until you resolve the problem.
Hope this helps you to start trouble shooting the problem.
I am trying to incorporate the RH control of interior air into the model (see attached model). I built the model for single zone and followed the available recommendations in the documentation and online to setup properly the RH control of the interior space. I made the model up and running but do not see effect of incorporated control on RH profile in interior space. Would appreciate any suggestions or hints to go around this problem.
Staff II - Building Technology
SIMPSON GUMPERTZ & HEGER
| Engineering of Structures and Building Enclosures
41 Seyon Street, Bldg. 1, Suite 500
Waltham, MA 02453