The Fraction of Supply Air Flow That Goes Through the Controlling Zone is automatically calculated by the program. It means that the thermostat zone, the zone that is defined in the input, provides all the air (fraction of air to the control zone divided by the total air flow rate through the heat pump). If you have more than 1 zone (or air terminal) on this air loop, then this air loop is not set up correctly. If you do only have 1 zone for this air loop, then this warning is a mistake and should probably not be written to the error file. If you do only have 1 zone, send your input file to energyplus-support@xxxxxxxx.
On 6/2/2011 10:32 PM, Vinay Devanathan wrote:
-- Richard A. Raustad Senior Research Engineer Florida Solar Energy Center University of Central Florida 1679 Clearlake Road Cocoa, FL 32922-5703 Phone: (321) 638-1454 Fax: (321) 638-1439 or 1010 Visit our web site at: http://www.fsec.ucf.edu UCF - From Promise to Prominence: Celebrating 40 Years
Primary EnergyPlus support is found at:
http://energyplus.helpserve.com or send a message to energyplus-support@xxxxxxxx
The primary EnergyPlus web site is found at:
The group web site is:
Attachments are currently allowed but be mindful that not everyone has a high speed connection. Limit attachments to small files.
EnergyPlus Documentation is searchable. Open EPlusMainMenu.pdf under the Documentation link and press the "search" button.