E+ does support primary / secondary, but does not support a variable speed pump on the primary side (use constant speed)
James V Dirkes II, PE, BEMP, LEED AP
Hi, all group, i need some help!
I got this warning when i try to simulate a Primary and secondary both variable pumps in Chiller water systems (The chiller incorporate VFD):
** Warning ** SetupCommonPipes: detected variable speed pump on supply inlet of TwoWayCommonPipe plant loop
It seems that Commonpipesimulation in Plant Loop doesn't simulate primary and secondary variable pumps.
There is any way to could model primary and secondary variable pumps??
Primary EnergyPlus support is found at:
http://energyplus.helpserve.com or send a message to energyplus-support@xxxxxxxx
The primary EnergyPlus web site is found at:
The group web site is:
Attachments are currently allowed but be mindful that not everyone has a high speed connection. Limit attachments to small files.
EnergyPlus Documentation is searchable. Open EPlusMainMenu.pdf under the Documentation link and press the "search" button.