You can read the documentation,the engineering reference pdf file.It has the chiller models very well explained.
I have also uploaded an spreadsheet to the yahoo group which leads you to obtain the three curves after providing the performance chiller data values.
I hope this can help you.
---------- Forwarded message ----------
Date: Tuesday, 31 July 2012
Subject: [EnergyPlus_Support] cop and iplv values of a chiller, also i have the part load performance
I have the cop and iplv values of a chiller, also i have the part load performance values of
EEFT Evaporator entering fluid temperature
ELFT Evaporator leaving fluid temperature
CEFT entering condenser water temperature
CLFT leaving condenser water temperature
for each part load(15,20,30...100%)
I dont know how to set it or how to transform it to can set this values in energy+, i think that the program could generate a curve with only COP and IPLv but i havent cant find that. Also i have tried to use Chiller:EIR and the EIRPLR curve is:
EIRFPLR y = 1.9927x2 - 1.9632x + 1.0078
RÂ² = 0.9499
i dont know if it is correct, also i dont know set up the other 2 curves because both are for full load, well, i think that because there ae onl function of temperatures.
thank you in advance.