[Equest-users] Sizing of equipment
Brahme, Rohini UTRC
BrahmeR at utrc.utc.com
Tue Jan 13 08:25:06 PST 2009
Check for reverse acting thermostat, or make sure that your min-air flow
for heating is sufficient.
From: equest-users-bounces at lists.onebuilding.org
[mailto:equest-users-bounces at lists.onebuilding.org] On Behalf Of
Sent: Tuesday, January 13, 2009 11:03 AM
To: equest-users at lists.onebuilding.org
Subject: [Equest-users] Sizing of equipment
I am running a load with many zones on 5 floors totaling over 300 zones.
There are some zones with many unmet hours, some of the core, some
perimeter. I went in and changed the sizing ratio of these zone to
reduce the unmet heating hours. I am modeling this building with 9
AHU's, all VAV w/ reheat. Does anyone have any insight or suggestions on
why or how these unmet hrs. exist. I have changed the hot water loop
flow GPM but it had no effect on the unmet heating hrs. so I deduced
this is not the cause.
Janne Kairento, E.I.T., LEED AP
Cambridge, MA 02142
Please consider the environment before printing this e-mail
NOTICE OF CONFIDENTIALITY This E-mail message and its attachments (if
any) are intended solely for the use of the addressees hereof. In
addition, this message and the attachments (if any) may contain
information that is confidential, privileged and exempt from disclosure
under applicable law. If you are not the intended recipient of this
message, you are prohibited from reading, disclosing, reproducing,
distributing, disseminating or otherwise using this transmission.
Delivery of this message to any person other than the intended recipient
is not intended to waive any right or privilege. If you have received
this message in error, please promptly notify the sender by reply E-mail
and immediately delete this message from your system.
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Equest-users