[Equest-users] 答复: Thermal storage modeling issues: high cooling capacity and unmet hours
mayank.23aug at gmail.com
Mon Apr 28 03:11:59 PDT 2014
Thank you for valuable suggestions.
However, the model with thermal storage still have unmet hours. I checked
peak building load annually and monthly (LS-C and LS-D report) and found no
change in peak load.
Please guide me to overcome this problem.
On Fri, Apr 25, 2014 at 6:37 AM, Tan, Kevin Zong-Neng <tan.kevin at pbworld.com
> Pls check your charging sch & discharging sch, this may help.
> *发件人:* Mayank Bhatnagar [mailto:mayank.23aug at gmail.com]
> *发送时间:* 2014年4月24日 13:29
> *收件人:* equest-users at lists.onebuilding.org
> *主题:* [Equest-users] Thermal storage modeling issues: high cooling
> capacity and unmet hours
> Dear eQuest users,
> I need help in thermal storage modelling. The issue which I have faced is:
> The project have 4 chiller (2200 TR each). To reduce peak load in day
> time, I have modeled thermal storage of 8000 TR-h (95 MBTU) with charging
> and discharging rate at 11.9 MBTU/h and 12 MBTU/h. To size each chiller
> capacity, I modeled chillers as autosize in both case (with and without
> thermal storage).
> When there is no thermal storage the chiller sizing is 2386 TR each (4
> chiller) with zero unmet hours and When I modeled thermal storage and a
> chiller dedicated to thermal storage and other three are working as
> supporting to thermal storage. The chiller size in this case are 3 chillers
> of 3496 TR and one chiller of 1026 TR and 5467 unmet hours.
> I am following procedure as mentioned in tutorial (attached). However, I
> got unmet hours and higher cooling tonnage than without thermal storage
> Please help me to sort out this problem.
> Mayank Bhatnagar
> Energy Analyst
> NOTICE: This communication and any attachments ("this message") may
> contain confidential information for the sole use of the intended
> recipient(s). Any unauthorized use, disclosure, viewing, copying,
> alteration, dissemination or distribution of, or reliance on this message
> is strictly prohibited. If you have received this message in error, or you
> are not an authorized recipient, please notify the sender immediately by
> replying to this message, delete this message and all copies from your
> e-mail system and destroy any printed copies.
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Equest-users