[Equest-users] FW: entering a balance point into eQuest
bfountain at greensim.com
Wed May 21 16:16:58 PDT 2014
What you can do is set the hot water loop operation to SNAP and have it set
to an outdoor air temperature of 47F. That will disable your hot water loop
for hydronic heating when the outdoor temperature is above 47F. (This is in
the detailed interface, not the wizard).
From: Equest-users [mailto:equest-users-bounces at lists.onebuilding.org] On
Behalf Of Sol Rosenbaum
Sent: Wednesday, May 21, 2014 5:50 PM
To: equest-users at lists.onebuilding.org
Subject: [Equest-users] entering a balance point into eQuest
>From discussion with the site contacts and some of the data we pulled from
the management's EMS system, we know that the building's balance point is 47
degF outdoor air temperature. Above that temperature, no heat is required
in the building.
Is there a place to enter this into eQuest so that it will be able to know
when the heating hours required based on the temperature data?
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Equest-users