[Hap-users] help with load calculation
Systems, Software CCS
Software.Systems at carrier.utc.com
Fri Nov 9 03:41:32 PST 2012
In order to assist, we will need your account information.
Please let us know your company name, address, and phone number you are licensed under.
Upon receipt, we can verify and have our tech support team respond.
Carrier Software Support
From: hap-users-bounces at lists.onebuilding.org [mailto:hap-users-bounces at lists.onebuilding.org] On Behalf Of dele omotayo
Sent: Thursday, November 08, 2012 6:07 PM
To: Hap-users at lists.onebuilding.org
Subject: [Hap-users] help with load calculation
I have a project which requires a different system for cooling and fresh air and the two system are to be fed from a chller plant.After adding the spaces, it was observed that the total coil load being generated from the system is quite lower than the load generated from the cooling plant summary being generated from the plant. my expectation was to have an approximately equal load since it is thesame system that was being added to the plant system .contrarily the generated system load is like one-third of the generated system load.
equipment type; terminal unit
Air system type; 2 pipe fan coil
Generic chiller plant
I need to know if this result is normal and a justification for the variation.
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the Hap-users