I want to apologise because I found another error in my file.
How could I want the setpoints to work (I want to maintain a temperature between 20-23) if I choose Single Heating and Single Heating instead of Dual Setpoint???
I am not using all my brain.I am runnig the file now to check the heating and cooling loads.
I read in previous e-mail that there is a problem with load convergence criteria in heating/cooling loads.
I was obtaining high loads in certain hours in the previous file I send.Could this be because of that?Maybe with the correction of setpoints the loads decrease.
To unsubscribe from this group, send an email to:
The primary EnergyPlus web site is found at:
The group web site is:
Your use of Yahoo! Groups is subject to the Yahoo! Terms of Service.