[Date Prev][Date Next][Thread Prev][Thread Next][Date Index][Thread Index]
Thank you very much for your reply!
But I have another question. There are eight cooling coil in my
idf, and each cooling coil belong to one Air Primary Loop.
In the result of my simulation, I find the Water MassFlowRate
through one of the cooling coil is zero at any time,so the Mean Air
Temperature in one zone is too high. The other cooling coil and Loop
works well. I can not explain it. Can you give me a hint? Thanks a
The primary EnergyPlus web site is found at:
The group web site is:
Attachments are not allowed -- please post any files to the appropriate folder in the Files area of the Support Web Site.
Yahoo! Groups Links
<*> To visit your group on the web, go to:
<*> To unsubscribe from this group, send an email to:
<*> Your use of Yahoo! Groups is subject to: