[Date Prev][Date Next][Thread Prev][Thread Next][Date Index][Thread Index]
[EnergyPlus_Support] About the zone temperature
I used a electric chiller to serve six Fan Coil Unit: 4 pipe for
conditioning six different thermal zones. All the fan coil units are
autosized, and the zone temperature set to 24C during the conditioning
time. But the design day simulation results shows that the zone
temperature in three zones floats up to 26C, while the temperature of
the other three zones retains 24C.
I think the chiller has adequate cooling capacity. I did not use
any controller to distribute the chilled water to fan coil unit.Because
the HVAC system is composed of fan coil units and chiller. How can I
increase the chilled water flow rate for the three heater zones ?
The primary EnergyPlus web site is found at:
The group web site is:
Attachments are not allowed -- please post any files to the appropriate folder in the Files area of the Support Web Site.
Yahoo! Groups Links
<*> To visit your group on the web, go to:
<*> To unsubscribe from this group, send an email to:
<*> Your use of Yahoo! Groups is subject to: