Your ground loop is probably too small. For a closed loop GSHP system - you can expect the ground loop temperature to fall to quite low levels -that's how they work. The output of your heat pump then falls - and the auxiliary heating kicks in. So - make sure you have a big enough heat pump, at the lowest EWT (entering water temperature) from the ground.
Tel: +44 (0) 1326 211070 Fax: +44 (0) 1326 212754 Web: www.geoscience.co.uk
Registered Office: Falmouth Business Park, Bickland Water Rd, Falmouth, TR11 4SZ, UK
Registered in England No 1930745
IMPORTANT NOTICE: This email is confidential, may be legally privileged, and is for the intended recipient only. Access, disclosure, copying, distribution or reliance on any of it by anyone else is prohibited and may be a criminal offence. If you have received this e-mail in error please inform the sender and delete it from your mailbox or any other storage mechanism. Any communication of a personal nature in this message is not made by or on behalf of any GeoScience Group company. Please note that the sender?s e-mail address and all other GeoScience group e-mail addresses are not valid addresses for the service of legal proceedings.