[Date Prev][Date Next][Thread Prev][Thread Next][Date Index][Thread Index]
[EnergyPlus_Support] Regarding the problem of Cooling Coil sizing
- To: energy software <EnergyPlus_Support@xxxxxxxxxxxxxxx>
- Subject: [EnergyPlus_Support] Regarding the problem of Cooling Coil sizing
- From: sheelam khare <sheelam_khare_26@xxxxxxxxxxx>
- Date: Mon, 3 Jun 2013 00:02:02 +0800 (SGT)
- Delivered-to: mailing list EnergyPlus_Support@xxxxxxxxxxxxxxx
- Delivery-date: Sun, 02 Jun 2013 10:02:11 -0600
- Dkim-signature: v=1; a=rsa-sha256; c=relaxed/relaxed; d=yahoogroups.com; s=echoe; t=1370188930; bh=uPYvnA8QaWfoyP/Ywwph2OFgn0a7+LhoarBRVj0cXA4=; h=Received:Received:X-Yahoo-Newman-Id:X-Sender:X-Apparently-To:X-Received:X-Received:X-Received:X-Received:X-Received:X-Received:X-Received:X-Received:X-YMail-OSG:X-Received:X-Rocket-MIMEInfo:X-Mailer:References:Message-ID:To:X-Originating-IP:X-eGroups-Msg-Info:From:X-Yahoo-Profile:Sender:MIME-Version:Mailing-List:Delivered-To:List-Id:Precedence:List-Unsubscribe:Date:Subject:Reply-To:X-Yahoo-Newman-Property:Content-Type; b=FceYLNTX2DSzw1jjzy8Swedett4efzxrf5IuZHcQCqd+r0h6NtER9JnuU0ow2ZK0WquFsZXIv88q+WIiGBeQKQDoBzTpMXMy+In8KEXJQ+T8yNWgHJXN3gozGVZOdlOuYdyzyvqp5WP9cAjyVl43okuGa/PWYA+nnVbYg9TNCtI=
- Domainkey-signature: a=rsa-sha1; q=dns; c=nofws; s=echoe; d=yahoogroups.com; b=dwm2LKdQQsP/ALHTzJDokAkMn79gq0eBnrVPtUksPxRMerI49jCQ06D7tR46JFwznhXI9TlQz2VEUG7EN4k67IlWF6jgLOLNUnigpny/tYRuvk0OjPyeaAfDqbnL8h/505YBWJlDthGurXH/jOpKBOOI+/bNcp2XX1L8VatyYdw=;
- Envelope-to: linda@xxxxxxxxxxxxxx
- List-id: <EnergyPlus_Support.yahoogroups.com>
- List-unsubscribe: <mailto:EnergyPlus_Supportemail@example.com>
- Mailing-list: list EnergyPlus_Support@xxxxxxxxxxxxxxx; contact EnergyPlus_Support-owner@xxxxxxxxxxxxxxx
- Reply-to: EnergyPlus_Support@xxxxxxxxxxxxxxx
- Sender: EnergyPlus_Support@xxxxxxxxxxxxxxx
I am trying to simulate a building located at Barcelona, Spain for LEED NC certification. During simulation I am facing the problem of cooling coil sizing. After running the simulation, the following waring is appears many time with respect to all the zones-
** Warning ** SizeDXCoil: Coil:Cooling:DX:SingleSpeed BLOQUE1:A3%SECRETARIA PTAC COOLING
** ~~~ ** ...Rated Total Cooling Capacity will be limited by the minimum rated volume flow per rated total capacity ratio.
** ~~~ ** ...DX coil volume flow rate (m3/s) = 7.229479E-002
** ~~~ ** ...Requested capacity (W) = 2192.909
** ~~~ ** ...Requested flow/capacity ratio (m3/s/W) = 3.296E-005
** ~~~ ** ...Minimum flow/capacity ratio (m3/s/W) = 4.027E-005
** ~~~ ** ...Adjusted capacity (W) = 1795.252
I tried to solve this but did not find the right solution.
Please give your suggestions, your suggestions are very helpful for me.
Thanks with regards..
Primary EnergyPlus support is found at:
http://energyplus.helpserve.com or send a message to energyplus-support@xxxxxxxx
The primary EnergyPlus web site is found at:
The group web site is:
Attachments are currently allowed but be mindful that not everyone has a high speed connection. Limit attachments to small files.
EnergyPlus Documentation is searchable. Open EPlusMainMenu.pdf under the Documentation link and press the "search" button.