[TRNSYS-users] Heating/cooling energy consumption (David BRADLEY)
shahinrkl_7 at yahoo.com
Wed Mar 5 02:39:59 PST 2014
I am trying to select the heating and cooling system size, as well as to get the load file that will be used later in another project, through simulation of a house.
However, I have only sensible gain or latent gain in the type 56. So how can I find the total gain or demand.
Could you please advise me
On Monday, March 3, 2014 10:05 PM, "trnsys-users-request at cae.wisc.edu" <trnsys-users-request at cae.wisc.edu> wrote:
----- Forwarded Message -----
Send TRNSYS-users mailing list submissions to
trnsys-users at cae.wisc.edu
To subscribe or unsubscribe via the World Wide Web, visit
or, via email, send a message with subject or body 'help' to
trnsys-users-request at cae.wisc.edu
You can reach the person managing the list at
trnsys-users-owner at cae.wisc.edu
When replying, please edit your Subject line so it is more specific
than "Re: Contents of TRNSYS-users digest..."
1. Re: Heating/cooling energy consumption (David BRADLEY)
2. Re: Capacitance clarification in TYPE536 (David BRADLEY)
3. Re: Type 604 - end of time step (David BRADLEY)
Yes, you care correct on both counts. You can also ask Type56 to
give you QCOOL as an output if you want to know cooling loads. Keep
in mind that the loads are sensible only and that no latent loads
are calculated unless you have activated either humidification or
dehumidication in a zone.
On 2/26/2014 07:22, Igor Seso wrote:
>I want to simulate/calculate the heat energy consumption of a building Type 56 (weekly,monthly).
>1.Since as output from the TYPE 56 I get only the Qheat_zone (heat transfer rate-power) so will it be correct to use the quantity integrator type 24 and connect with Type 46?
>2. For the integration period if I put 24 hr does it mean that I get daily energy consumption? and with STOP I get for the whole simulation period?
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the TRNSYS-users